CABINET—Powder coat painted. Matching discharge plenums and decorative supply and return air grilles are available for use when units are to be installed within conditioned space.
MOTOR—Inherently protected motors are mounted inside of insulated cabinet to reduce motor noise and provide a neat looking installation. A choice of motor horsepowers and drive combinations are available to allow you to meet specified CFM at various static pressures. Motors and mounts and units may be relocated in field to opposite side of blower scroll for accessibility.
LOW PROFILE—Allows for horizontal installation in most standard drop ceiling applications, and the movement of units through most standard doorways for addition or replacement work.
THERMAL EXPANSION VALVES—Standard all models. Throwaway filters are standard, but filter racks are designed to accept either one inch or two inch filters.
EVAPORATOR COIL—Two circuit, interlaced row split coils are constructed with copper tubes and aluminum fins mechanically bonded to the tubes for maximum heat transfer capabilities. All coil assemblies are leak tested prior to installation into units.
REFRIGERANT CONNECTIONS—Field piping connections are made through a fixed post between two side access panels on either side of the unit. Allows flexibility to meet most field conditions as well as full accessibility after the installation is complete. Units may be used with two straight cool condensing units or single circuit manifolded in the field using the copper fittings shipped with each unit.
DRAIN PAN—The galvanized steel drain pan is designed to trap condensate in either vertical or horizontal installations. Condensate drain connections are located on both sides of the unit allowing complete flexibility to meet most field conditions.
SERVICE ACCESS—Two removable panels on top and each side of the unit are easily removed for access to motors, blowers, sheaves, and filters.
HORIZONTAL OR VERTICAL—All models are designed for either application and can be installed in either position as supplied from the factory.
TESTING—All units are run tested at the factory prior to shipment. Units are shipped with a holding charge of nitrogen.